Issue 
Sci. Tech. Energ. Transition
Volume 79, 2024
Decarbonizing Energy Systems: Smart Grid and Renewable Technologies



Article Number  25  
Number of page(s)  11  
DOI  https://doi.org/10.2516/stet/2024017  
Published online  05 April 2024 
Regular Article
Economic dispatch of communityintegrated energy system considering demandside coordinated response
State Grid Beijing Electric Power Research Institute, Beijing 100075, PR China
^{*} Corresponding author: 13856673123@163.com
Received:
24
November
2023
Accepted:
28
February
2024
There are a large number of potential schedulable resources in the integrated energy system of electricity, heat, cold, and gas. However, most of these energy sources are currently operated separately, with low system flexibility, low energy utilization rate, and serious abandonment of wind and solar energy. In order to improve the flexibility of integrated energy systems and the capacity of renewable energy consumption, an economic dispatch of communityintegrated energy systems considering demandside coordinated response is proposed. Firstly, according to various energy characteristics, mathematical models of various energy forms are established, including wind energy, photovoltaic, gas turbine, gas boiler, and other component characteristics modeling. Secondly, an economic optimal scheduling model of communityintegrated energy system considering demand side response is established, including the constraints and objective functions of the optimization model, and the optimization model is solved based on the Yalmip toolbox and Cplex solver in Matlab software. Finally, the effectiveness of the proposed strategy is verified by a simulation example.
Key words: Integrated energy system / Demandside coordinated response / Economic optimal scheduling model / Yalmip toolbox / Cplex solver
© The Author(s), published by EDP Sciences, 2024
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (https://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
1 Introduction
Electrical energy consumption is necessary for all areas of modern life, covering households, enterprises, construction, farming, teaching, medicine, research, and innovation [1]. The installed capacity of new energy sources such as wind turbines and photovoltaics is increasing year by year [2–4]. At the same time, industrial, commercial, and residential users need more and more forms of capacity, but most of these energy systems are currently operating separately [5]. The separate operation of power, heat, cold, and gas energy systems leads to low system flexibility, low energy utilization rate, and serious abandonment of wind and light. The combined scheduling of electric heating and cooling gas is a little obvious, which can effectively improve the operation efficiency of the whole system, reduce the waste of different energy sources, reduce the operation cost of the system, and improve the stability and flexibility of the system [6].
To balance social development and environmental protection, it is urgent to seek the optimization of energy structure and the efficient use of energy [7, 8]. In recent years, the integrated energy system has developed rapidly [9]. Integrated Energy Systems (IES) refers to the coupling of electricity, gas, heat, cold, and other energy sources, which can effectively improve energy utilization efficiency and promote sustainable energy development while meeting the diversified energy use needs of the system. Compared with the traditional distributed energy system, the integrated energy system is a complex system that includes a variety of energy sources, such as electricity, gas, heat, etc. Specifically, the system contains a variety of different energy resource inputs, and has many different forms of output and transportation, is a regional energy interconnection system. It is not just a simple superposition of multiple resources, but at the system level, for the comprehensive complementary use of different energy sources, coordinate the mutual conversion between various energy sources, to achieve the most reasonable results and benefits [10]. The coordinated and sustainable development of multienergy systems is the inevitable trend of the development of integrated energy systems in the future. Therefore, integrated energy systems have broad development prospects.
At present, the potential of integrated energy systems is increasing [11, 12]. In the aspect of IES model construction, according to the difference between load and equipment output, Power to Gas (P2G) technology and gas turbine technology are used to cut peak and fill valley in the literature [13], and the index of peak shaving and valley filling is introduced into the objective function, and the optimization is established. In reference [14], the multienergy complementary strategy was used to increase the consumption of renewable energy. The IES system including the coupling of cogeneration units and electric heating equipment was studied, and the energy storage characteristics of the heating network were considered. Literature [15] established a multiobjective IES scheduling model and a realtime demand response model based on energy prices. Reference [16] pointed out that it is limited to relying solely on the energy storage system for regulation. Therefore, on this basis, a composition of electricity, heat, and hydrogen is proposed. In [17, 18], for multienergy complementary systems, the minimum sum of energy purchase cost and operation and maintenance cost is taken as the objective function of the system, and the corresponding optimal scheduling model is established. Reference [19] constructed an integrated energy system of “coldheatelectricitygas”, and established an operation optimization model of regionally integrated energy systems with the objective function of net profit, energy utilization efficiency, and load matching of regionally integrated energy systems. In literature [20], a comprehensive energy system containing electric, hot, and cold systems was studied. At the same time, it is proposed that the flexible load in the integrated energy system participates in the optimal operation of the system. However, the modeling methods for flexible loads of electric, hot, and cold were single, and the differences in energy use characteristics between loads were not taken into account. Literature [21] puts forward energy management strategies to reduce IES operating costs, establishes flexible electrical and thermal load models, and divides electrical loads into two types: transferable load and reducible load.
Inspired by the aforementioned issues, this paper proposes an economic dispatch of community integrated energy system considering a demandside coordinated response. Firstly, mathematical models of various energy forms are established according to various energy characteristics, including fan, photovoltaic, gas turbine, gas boiler, and other component characteristics modeling. Secondly, the multienergy complementary optimization model including electricity, cold, and hot energy forms is established, and the loadside demandside response is taken into account. Finally, Matlab software Yalmip toolbox and Cplex solution are used to solve the optimization model, and the concrete expression of energy Internet multienergy complementarity is given.
2 Integrated energy system composition
The schematic diagram of the regional integrated energy system is shown in Figure 1, which mainly includes three energy subsystems: electricity, cold, and heat. Among them, the power grid, gas turbine, photovoltaic power supply, and gas boiler are the energy input of the integrated energy system; The electric boiler can convert electrical energy into thermal energy, the electric refrigerator can convert electrical energy into cold, and the absorption refrigerator is the liaison element of the cold and hot system, and the three liaison elements realize the mutual conversion between various energy sources within the integrated energy system. The load types are generally divided into flexible load and rigid load. The flexible load can participate in the demand side response of the integrated energy system, while the rigid load cannot. The flexible load can be divided into translation load, reduction load, and transfer load.
Fig. 1 Integrated energy system composition. 
3 Multienergy complementary optimization operation scheduling model of regional integrated energy system
The multienergy complementary preday optimization operation scheduling model of the regional integrated energy system, which includes electricity, cold and hot energy, is established to optimize the preday optimization operation of the integrated energy system according to the predicted output and load information of photovoltaic and other new energy sources, making the integrated energy system run economically. In the field of optimization, the optimal scheduling model belongs to the category of planning problems. A complete optimization model includes the constraints of the optimization model, the objective function of the optimization model, and the decision variables of the optimization model, which will be analyzed in detail later. Constraints of multienergy complementary optimization operation model of regionally integrated energy system containing electric, cold, and hot energy.
3.1 Constraint conditions of multienergy complementary optimization operation model for regional integrated energy system
 1.
Power grid purchase and sale capacity constraints
The integrated energy system cannot purchase or sell electricity to the power system in excess of the maximum allowable power value of the line, that is(1)where P_{link.max} is the maximum running power of the line; α_{pur}(t), α_{cell}(t) indicates the status of power purchase and sale; P_{sur}(t) is the power purchased from the grid; P_{sell}(t) is the amount of power sold to the grid.
 2.
Constraints on the output capacity of photovoltaic and winddistributed power supplies
The maximum active power output of the photovoltaic power supply cannot exceed the capacity of the photovoltaic power supply, that is(2) (3)where P_{pv} is photovoltaic active power output; P_{wind} is wind active power output; S_{pv} is the capacity of photovoltaic power supply; S_{wind} is the capacity of wind power supply.
 3.
Gas turbine operating constraints
Gas turbines mainly generate electricity and heat energy through natural gas, and the relationship between electric power and thermal power is(4)where Q_{GT}(t) is the heat generated by the gas turbine; P_{GT} is the electric power output of the gas turbine; η_{GT} is gas turbine efficiency; η_{l} is the heat loss coefficient of the gas turbine.
At the same time, gas turbines consume natural gas while generating electric energy and heat energy, and the relationship between the amount of natural gas consumed and the output power is shown in the equation(5)where V_{GT}(t) is gas turbine volume consumption; L_{NG} is the low calorific value of natural gas; Δt is the scheduling interval.
At the same time, considering that the gas turbine output cannot exceed its upper limit and lower limit, that is(6)where P_{GT.min} is the minimum output of the gas turbine; P_{GT.max} is the maximum output of the gas turbine; P_{GT} is the output power of the gas turbine.
Gas turbine output should also meet the upward and downward climbing speed, that is(7)where r_{GT.up} and r_{GT.down} are the maximum upanddown climbing speeds of gas turbines.
 4.
Fuel cell operating constraints
Fuel cell output constraints should be met(8)where P_{FC}(t) is the fuel cell output at time t; P_{FC.max}, P_{FC.min} are the maximum/minimum output power of the fuel cell.
The constraint on the maximum up and down climb rates is(9)where r_{FC.up} and r_{FC.down} are the maximum upanddown climbing speed of the fuel cell.
 5.
Gas boiler operation constraints
The output of the gas boiler cannot exceed the upper and lower limits of the output, so it should be met(10)where Q_{GB.max} is the upper limit of gas boiler output; Q_{GB.min} is the lower limit of gas boiler output; is the variable 0–1, 1 indicates the on state, 0 indicates the off state.
The maximum ascending and descending climbing speed constraints are(11)where r_{GB.up} and r_{GB.down} indicate the maximum climbing speed of the gas boiler.
 6.
Electric boiler operation constraints
The electric boiler input should be less than its maximum input power, that is(12)where is the maximum input power of the electric boiler; is the input power of the electric boiler.
The constraint on the maximum up and down climb rates is(13)where r_{EB.up} and r_{EB.down} indicate the maximum climbing speed of the electric boiler.
 7.
Operation constraint of electric refrigerator
The output cold power of the electric refrigerator cannot exceed the maximum output power of the electric refrigeration(14)where is the maximum output power of the electric refrigerator; is the output power of the electric refrigerator.
The constraint on the maximum up and down climb rates is(15)where r_{EC.up} and r_{EC.down} indicate the maximum climbing rates of the electric refrigerator.
 8.
Operating constraints of absorption chillers
Absorption chillers supply the cold load of the integrated energy system, and the output cold power should be within the limit value, that is(16)where is the maximum output power of the absorption refrigerator; is the output power of the absorption refrigerator.
The output power of the absorption refrigerator is also affected by the climbing speed, that is(17)where r_{AC.up} is the maximum ascending climbing speed of the absorption refrigerator; r_{AC.down} is the maximum downward climbing speed of the absorption refrigerator.
 9.
Constraints on the operation of the energy storage device
Take the battery as an example. Overcharging and overdischarging of the battery will affect the operating state of the battery. Therefore, the limit of the charged state of the battery must be within the safe and reliable range, that is(18)where S_{BAT.max} and S_{BAT.min} are the safe upper and lower limits of the battery charging state.
A battery can work in only one state at a time(19)where , the variable 0–1, 1 indicates the on state, 0 indicates the off state.
When the battery participates in the optimization operation of the integrated energy system, the state of charge needs to be equal at the beginning and end of the dispatching cycle, that is(20)where is the charged state of the battery at the beginning of the scheduling cycle when the battery participates in the optimization operation of the integrated energy system.
To ensure the working lifetime of the battery and improve the overall operation economy and reliability of the comprehensive energy system, the battery cannot be charged and discharged too much.(21)where E_{BAT} indicates the rated capacity of the battery; is the charging power of the battery in the i period; is the discharge power of the battery in the i period; is the variable 0–1, indicating whether the battery is in the charging state. 1 indicates that the battery is in the charging state, and 0 indicates that the battery is in the noncharging state. is the variable 0–1, indicating whether the battery is in the discharge state. 1 indicates that the battery is in the discharge state, and 0 indicates that the battery is not in the discharge state.
Similarly, the charge and discharge times of the battery will affect the operating lifetime of the battery, and then affect the overall equipment investment cost of the comprehensive energy system, so it is necessary to control the charge and discharge times of the energy storage equipment to ensure the working time of the energy storage equipment.(22)where is the safe charging times of energy storage equipment; is the safe discharge times of the energy storage device.
 10.
Translational load constraint
Translation load is a kind of flexible load, which can be translated into the whole section to relieve the load pressure of the integrated energy system in a certain period of time. Taking translatable load L_{shift} as an example, L_{shift} can be represented by a set of vectors with a certain continuity, where t_{s} is the initial time of the translatable load and t_{D} is the continuous time of the translatable load.(23)
It is assumed that the time interval to which the shiftable load can be shifted is [t_{sh}, t_{sh}+1,...,t_{sh+}]. Considering that the shiftable load needs to be shifted as a whole, the initial value of the shiftable time interval must be satisfied. If it is not satisfied, some of the shiftable load will exceed the shiftable time interval.(24)
Whether load translation is carried out at the initial value can be expressed by the vector , indicates that load translation is carried out at this initial value, and indicates that no load translation is carried out at this initial value.(25)where indicates the shift load in period i; indicates no shift load in period i.
In order to facilitate the integrated energy system scheduling, the shiftable load generally carries out only one shift, so should meet the constraint.(26)
 11.
Transferable load constraint
Transferable load means that the load of a certain period can be transferred to another period, to achieve the purpose of peak cutting and valley filling. Taking transferable load L_{tran} as an example, X ^{tran} indicates whether load transfer is performed in the corresponding period, indicates that load transfer is performed in the period, and indicates that load transfer is not performed in the period.(27)
At the same time, the transfer power will have certain constraints, and the transfer load cannot be completely transferred, so as not to affect the daily life of users in the park, so the constraints should be met(28)where is the transferable maximum; is a transferable minimum.
If the duration of the transferable load is not limited, the frequency of switching of electrical equipment in the park will be frequent, and the operating life of the user’s electrical equipment will be affected. In this regard, it is necessary to limit the minimum duration of the transferable load, that is(29)
Since the transferable load operation only transfers the load but does not reduce the load, the total load before and after the load transfer will not change(30)where is the total power before the transferable load is transferred.
 12.
Reducible load constraints
The reducible load refers to the direct cutting operation of the load to ensure the balance of supply and demand of the integrated energy system. Take L_{cut} as an example(31)
X ^{cut} indicates whether the load is reduced in the corresponding period, indicates that the load is reduced in the period, and indicates that the load is not reduced in the period.(32)
Load reduction will affect the comfort of users, taking the indoor building as an example, the reduction of cooling load will lead to excessive indoor temperature in summer; reducing the heat load will cause the indoor temperature to be too low in winter, which will lead to a poor user experience. Therefore, it is necessary to set the minimum duration of load shedding, the maximum duration of load shedding, and the upper limit of the number of load shedding.(33) (34) (35)
 13.
Power balance constraint of integrated energy system
Power balance constraints mainly include electric power balance, thermal power balance, and cold power balance. The electric power balance of the integrated energy system is shown in equation (36) (36)
The thermal power balance of the integrated energy system is shown as follows(37)where is the rigid heat load; is the transferable heat load; is reducible the heat load.
The cold power balance of the integrated energy system is shown as follows(38)where is the rigid cooling load; is the transferable cooling load; is reducible the cooling load.
The constraints of the multienergy complementary optimization operation model of the integrated energy system are shown in Table 1.
The constraints of the multienergy complementary optimization operation model.
3.2 Objective function of multienergy complementary optimization operation model for regional integrated energy system
The multienergy complementary optimization operation model of a regional integrated energy system containing electricity, cold, hot, and other energy sources aims at system cost. The daily cost of an integrated energy system includes system power purchase cost, distributed power supply operation cost, etc., so the objective function is(39)
 1.
Power purchase costs for integrated energy systems
The integrated energy system needs to buy electricity from the grid when it lacks power, and the integrated energy system can sell electricity to the grid when it has sufficient power, so the cost of unified power purchase of the integrated energy system within a dispatching cycle is related to the purchase and sale of electricity.(40)where is the purchase price from the power grid for the integrated energy system; is the price of electricity sold to the grid for the integrated energy system.
Therefore, the purchase cost of the integrated energy system is(41)
 2.
Photovoltaic, wind power supply operating costs
The distributed power supply in the integrated energy system is generally composed of photovoltaic, wind, and other new energy sources. In this paper, only photovoltaic and wind power are considered in the integrated energy system, and the total operation cost of photovoltaic and winddistributed power supply within a scheduling cycle is(42)where K_{wind} is the kilowatthour cost of winddistributed power supply; K_{pv} is the kilowatthour cost of photovoltaic distributed power supply.
 3.
Operating cost of gas equipment
The operating cost of gas equipment (gas turbine, gas boiler, and fuel cell) in one dispatching cycle is shown in the equation(43)where is the natural gas consumption of the gas turbine; K_{GT} is the KWH cost of the gas turbine; is the natural gas consumption of gasfired boilers; K_{GB} is the kilowatthour cost of the gasfired boiler; is the fuel cell gas consumption; K_{FC} is the kilowatthour cost of the fuel cell; K_{gas} is the cost of natural gas.
 4.
Operating costs of electric boilers, electric chillers, and absorption chillers
The operating costs of the electric boiler, electric chiller, and absorption chiller in one dispatching cycle are respectively(44)where K_{EB} is the operating cost factor of the electric boiler; K_{EC} is the operating cost factor of the electric refrigerator; K_{AC} is the operating cost factor of the absorption refrigerating machine.
 5.
The operating cost of energy storage equipment
Within a scheduling cycle, the operating cost of energy storage equipment (battery, heat storage tank, cold storage tank) is shown in the formula(45)where K_{cha} is the cost coefficient of energy storage equipment; K_{dis} is the discharge cost coefficient of the energy storage device. is the cost coefficient of a heat storage tank; is the cost coefficient of heat release in a heat storage tank; is the cost coefficient of filling a cold storage tank; is the cost coefficient of a cooling storage tank.
 6.
Shifting load compensation costs
The compensation costs of movable load (movable electrical load, movable thermal load, and movable cold load) are respectively(46)where is the cost coefficient of translatable load; is the total transferable electrical load; is the cost coefficient of transferable heat load, and is the total transferable heat load. is the cost coefficient of the translational cooling load, and is the total translational cooling load.
 7.
Transferable load compensation costs
where is the cost coefficient of transferable load.
 8.
Reducible load compensation costs
The compensation cost of the reduced load (the reducible electric load, the reducible heat load, and the reducible cold load) is(48)where is the cost coefficient of electric load that can be reduced; can reduce the cost factor of heat load; indicates that the cooling load cost factor can be reduced.
The objective functions of the multienergy complementary optimization operation model for a regional integrated energy system are shown in Table 2.
The objective functions of the multienergy complementary optimization operation model.
3.3 Regional integrated energy system multienergy complementary day optimization operation scheduling model to solve the overall process
The optimal operation scheduling model of a regional integrated energy system with electric, cold, and hot energy includes multiple energy forms and energy conversion, with many decision variables and large solution space. According to the daybefore forecast data of wind turbine output and load power, the controllable variables in the controllable components and flexible loads are taken as the decision variables, and the operation limitations of the controllable components, the supply and demand power balance in the system and the inherent limitations of the controllable load are taken as the constraint conditions, and the daily operating cost of the system is minimized as the optimization objective. Among them, the constraints of the optimization model have been introduced in detail in Section 3.2. The objective function of the optimization model has been introduced in detail in Section 3.1 of the paper. The proposed optimization model is a mixed integer programming model, in this regard, this paper uses the Yalmip toolbox and Cplex solver to solve the problem based on Matlab software, and the solution process is shown in Figure 2.
Fig. 2 The solution process of the optimal operation scheduling model. 
4 Case study
The forecast data of wind and PV output power are shown in Figure 3, and the time scale is set to 1 h.
Fig. 3 The forecast data of wind and PV output power. 
The forecast data for electrical load, thermal load, and cooling load are shown in Figures 4–6, and the time scale is 1 h.
Fig. 4 Predicted electrical load. 
Fig. 5 Predicted heat load. 
Fig. 6 Predicted cooling load. 
The price of natural gas is 3.23 ¥/m^{3}, the calorific value of combustion is 9.78 km/m^{3}, and the TOU price is shown in Figure 7.
Fig. 7 Time of use price. 
The interactive power with the power grid, wind power output, photovoltaic output, fuel cell output, gas turbine, and battery output is shown in Figure 8. It can be seen that the integrated energy system realizes the consumption of new energy and promotes the construction of a new power system through a variety of multienergy complementary coordination and optimization.
Fig. 8 Supply power to load each equipment output. 
The output thermal power of the gas boiler, gas turbine, electric boiler, and heat storage tank is shown in Figure 9.
Fig. 9 The output thermal power of gas boiler, gas turbine, electric boiler, and heat storage tank. 
The output of the absorption refrigerator, electric refrigerator, and cold storage tank is shown in Figure 10.
Fig. 10 The output of absorption refrigerator, electric refrigerator, and cold storage tank. 
Taking electrical load as an example, the changes in electrical load that can be shifted, transferred, reduced, and total electrical load are shown in Figures 11–14. It can be seen that by participating in the demand side response of the integrated energy system with a flexible load, the purpose of peak cutting and valley filling is achieved.
Fig. 11 Translational electric load. 
Fig. 12 Transferable electric load. 
Fig. 13 Reducible electric load. 
Fig. 14 Total electric load. 
5 Conclusion
In order to improve the flexibility of integrated energy systems and the capacity of renewable energy consumption, an economic dispatch of communityintegrated energy systems considering demandside coordinated response is proposed. Relevant conclusions are as follows:

Mathematical models of various energy forms are established according to various energy characteristics, including wind, photovoltaic, gas turbine, gas boiler, and other component characteristics modeling.

The multienergy complementary optimization model including electricity, cold, and hot energy forms is established, and the loadside demandside response is taken into account.

Through simulation results, it can be seen that by participating in the demand side response of the integrated energy system with flexible load, the purpose of peak cutting and valley filling is achieved.
At the same time, there are still some defects or limitations, which need to be further studied in the followup work, as follows:

The flexible load participates in the demand side response of the integrated energy system, and the influence of the change of the flexible load on the user’s electricity comfort in the integrated energy system is not considered, which needs further study.

There is still a certain gap between the optimization mathematical model proposed in this paper and the actual operation of the integrated energy system. At present, it is only a theoretical analysis and has not yet completed the followup landing.

The optimization mathematical model proposed in this paper is based on the accurate prediction of new energy power generation and load of integrated energy system, but there is still a gap with the actual operation, and the inaccuracy of prediction needs to be further considered in the followup.
Acknowledgments
This work was done by the State Grid Beijing Electric Power Company (5700202311602A32ZN).
References
 Goswami A.D., Hole S.R. (2024) Analysis and comparison of the DC–DC converter with soft computing algorithm, EAI Endorsed Trans. Scalable Inf. Syst. 11, 2, 1–8. [Google Scholar]
 Wang Y., Hu J., Liu N. (2023) Energy management in integrated energy system using energycarbon integrated pricing method, IEEE Trans. Sustain. Energy 14, 4, 1992–2005. [Google Scholar]
 Hole S.R., Goswami A.D. (2022) Quantitative analysis of DC–DC converter models: A statistical perspective based on solar photovoltaic power storage, Energy Harvest. Syst. 9, 1, 113–121. [Google Scholar]
 Hole S.R., Goswami A.D. (2023) Design of a novel hybrid soft computing model for passive components selection in multiple load Zeta converter topologies of solar PV energy system, Energy Harvest. Syst. 11, 1, 20230029. [Google Scholar]
 Shui Y., Liu J., Gao H., Qiu G., Xu W., Gou J. (2018) Twostage distributed robust cooperative dispatch for integrated electricity and natural gas energy systems considering uncertainty of wind power, Autom. Electric Power Syst. 42, 13, 43–50. [Google Scholar]
 Zhai J., Wu X., Zhu S., Yang B., Liu H. (2020) Optimization of integrated energy system considering photovoltaic uncertainty and multienergy network, IEEE Access 8, 141558–141568. [Google Scholar]
 Cao M., Shao C., Hu B., Xie K., Li W., Peng L., Zhang W. (2021) Reliability assessment of integrated energy systems considering emergency dispatch based on dynamic optimal energy flow, IEEE Trans. Sustain. Energy 13, 1, 290–301. [Google Scholar]
 Schick C., Klempp N., Hufendiek K. (2022) Role and impact of prosumers in a integrated energy system with high renewable shares, IEEE Trans. Power Syst. 37, 4, 3286–3298. [Google Scholar]
 Zhu S., Liu H., Xu J., Chen Z., Niu M. (2019) Study on the dayahead cooperation strategy of regional integrated energy system including CCHP, J. Eng. 2019, 18, 5219–5223. [Google Scholar]
 He J., Li Y., Li H., Tong H., Yuan Z., Yang X., Huang W. (2020) Application of game theory in integrated energy system systems: A review, IEEE Access 8, 93380–93397. [Google Scholar]
 Zhang Z., Zhang Y., Huang Q., Lee W.J. (2018) Marketoriented optimal dispatching strategy for a wind farm with a multiple stage hybrid energy storage system, CSEE J. Power Energy Syst. 4, 4, 417–424. [Google Scholar]
 Zhang S., Gu W., Yao S., Lu S., Zhou S., Wu Z. (2021) Partitional decoupling method for fast calculation of energy flow in a largescale heat and electricity integrated energy system, IEEE Trans. Sustain. Energy 12, 1, 501–513. [Google Scholar]
 Wei Z., Zhang S., Sun G., Zang H., Chen S., Chen S. (2017) Powertogas considered peak load shifting research for integrated electricity and naturalgas energy systems, Proc. CSEE 37, 16, 4601–4609. [Google Scholar]
 Gang L.I., Xiaodong W., Guangyi D. (2017) Multienergy complementary optimization research on local area integrated energy system, South. Energy Construct. 4, 2, 24–28. [Google Scholar]
 Saberi K., PashaeiDidani H., Nourollahi R. (2019) Optimal performance of CCHP based microgrid considering environmental issue in the presence of real time demand response, Sustain. Cities Soc. 45, 596–606. [Google Scholar]
 Diao H., Li P. (2020) Powertogas considered peak load shifting research for integrated electricity and naturalgas energy systems, in 12th IEEE PES AsiaPacific Power and Energy Engineering Conference (APPEEC), IEEE, Nanjing, China, pp. 1–5. [Google Scholar]
 Chen Z., Wang D., Jia H., Wang W.L., Guo B.Q., Qu B., Fan M.H. (2017) Research on optimal dayahead economic dispatching strategy for microgrid considering P2G and multisource energy storage system, Proc. CSEE 37, 11, 3067–3077. [Google Scholar]
 Liu R., Li Z., Yang X., Sun G., Li L. (2019) Optimal dispatch of community integrated energy system considering userside flexible load, Acta Energ. Sol. Sin. 40, 10, 2842–2850. [Google Scholar]
 Li R., Sun F., Liu H., Ding X., Han Y., Yan J. (2020) Economic dispatch with hybrid timescale of userlevel integrated energy system considering differences in energy characteristics, Power Syst. Technol 44, 10, 3615–3624. [Google Scholar]
 Chau T.K., Yu S.S., Fernando T., Iu H.H.C. (2017) Demandside regulation provision from industrial loads integrated with solar PV panels and energy storage system for ancillary services, IEEE Trans. Ind. Inform. 14, 11, 5038–5049. [Google Scholar]
 Jiang Z., Ai Q., Hao R. (2019) Integrated demand response mechanism for industrial energy system based on multienergy interaction, IEEE Access 7, 66336–66346. [Google Scholar]
All Tables
The objective functions of the multienergy complementary optimization operation model.
All Figures
Fig. 1 Integrated energy system composition. 

In the text 
Fig. 2 The solution process of the optimal operation scheduling model. 

In the text 
Fig. 3 The forecast data of wind and PV output power. 

In the text 
Fig. 4 Predicted electrical load. 

In the text 
Fig. 5 Predicted heat load. 

In the text 
Fig. 6 Predicted cooling load. 

In the text 
Fig. 7 Time of use price. 

In the text 
Fig. 8 Supply power to load each equipment output. 

In the text 
Fig. 9 The output thermal power of gas boiler, gas turbine, electric boiler, and heat storage tank. 

In the text 
Fig. 10 The output of absorption refrigerator, electric refrigerator, and cold storage tank. 

In the text 
Fig. 11 Translational electric load. 

In the text 
Fig. 12 Transferable electric load. 

In the text 
Fig. 13 Reducible electric load. 

In the text 
Fig. 14 Total electric load. 

In the text 
Current usage metrics show cumulative count of Article Views (fulltext article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 4896 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.